Please use this identifier to cite or link to this item:
|Title:||Optimal PMU placement using topology transformation method in power systems|
|Keywords:||Integer linear programming;Phasor measurement unit;Power flow measurements;Power system measurements;Topology, Zero-Injection Bus|
|Citation:||Journal of Advanced Research, (2016)|
|Abstract:||Optimal phasor measurement units (PMUs) placement involves the process of minimizing the number of PMUs needed while ensuring the entire power system completely observable. A power system is identified observable when the voltages of all buses in the power system are known. This paper proposes selection rules for topology transformation method that involves a merging process of zero-injection bus with one of its neighbors. The result from the merging process influenced by the selection of bus selected to merge with the zero-injection bus. The proposed method will determine the best candidate bus to merge with zero-injection bus according to the three rules created in order to determine the minimum number of PMUs required for full observability of the power system. In addition, this paper also considered the case of power flow measurements. The problem formulated as integer linear programming (ILP). The simulation for the proposed method tested by using MATLAB for different IEEE bus systems. The explanation of the proposed method is demonstrated by using IEEE 14-bus system. The results obtained in this paper proved the effectiveness of the proposed method since the number of PMUs obtained are comparable with other available techniques.|
|Appears in Collections:||Dept of Electronic and Computer Engineering Research Papers|
Items in BURA are protected by copyright, with all rights reserved, unless otherwise indicated.